ns am plan an electric home brewery. I have a 240 v outlet planned, if I run a 5500 watt element and also a pump have the right to it all be ~ above a 30 amp breaker? ns don't think I can I operation a 5500 watt and a 1600 watt aspect at the very same time, have the right to I?

You are watching: How many amps is a 5500 watt generator

Logged
StevieOfficial Poobah of No Life. (I obtained Ban Hammered by Drew)Posts: 6858

Full power that is 23 amps. Pumps have to be approximately an amp. Remainder of the panel shouldn’t be much depending upon what girlfriend do.No, you wouldn’t have the ability to run both. The smaller sized burner is going to it is in 120, so just have it be powered by one more circuit. V a 50a you can run both, yet your two warm legs would certainly be the end of balance (1600w aspect is 120 and only top top one warm leg). This is poor news as it could reason over heating.
Logged
russellAssistant BrewerPosts: 111
but the 240 v, 30 amp breaker might run the 5500 watt element along with the control box through a PID in it and pump cant it?
but the 240 v, 30 amp breaker could run the 5500 watt element together with the regulate box v a PID in it and pump cant it?

See more: What Does Mca Testing Stand For, Statewide Testing

First, make sure the breaker you select is GFCI or use a separate GFCI because that protection.Then, execute some math. Watts = Amps x Volts ... Therefore ... Amps = watts / VoltsBuild in a 15-20% safety factor on the breaker (local code regularly requires this).You're most likely really gaining closer come 220 volts 보다 240 volts from her utility.So, 5500 watts / 220 volts X 0.80 = 20 amps. If you have a 30-amp breaker, you should have plenty that amps to take care of the element, linked electronics (which frequently only attract a couple of hundred milliamps), and also probably a pair March or Chugger pumps, too. Including that second 1650-watt element would put you in ~ 26 amps - tho under 30, yet closer 보다 I'd treatment to be if running other accessories (pumps. Etc.). If you want to run two elements at the same time, you're probably far better advised to use a enlarge breaker. I have a 15-gallon 3-vessel device with a 5500-watt facet in the HLT and also another 5500-watt in the BK. The system likewise has 2 Chugger pumps. I operation both aspects at the exact same time because that back-to-back batches and/or to heat up cleaning solution while boiling. I have actually a 50-amp GFCI breaker because that the totality system with both pumps running, the HLT aspect at 100% and the BK element at 80%. Both elements at 100% would be 11,000 watt / 220 volts X 0.80 = 40 amps. So, the leaves another 8 amps at 220 volts come spare for the 120-volt pumps and also electronics.Also, don't overlook the you'll need heavier-gauge cable to take care of the higher amperage. I little the bullet and also had a licensed electrician download the breaker and also run the heavier-gauge cable come the 220/240-volt outlet.Be safe and have fun.Brew on!