Max. Cont. Power (LP): 8 kWMax. Cont. Power (NG): 7 kWMax. Cont. Amps (LP/NG): 33.3/29.2Main line Circuit Breaker: 35 AmpsPanel Fuse Type: 7.5 Amps ATOBattery Type: Group 26R, 12V, 540 CCAOil Type: Check chart in ManualOil Capacity: 1.5 QuartsOil Filter Type: Full flow spin-on cartridge Oil Filter P/N: 070185ESNG Consumption-50% : 78 ft^3/hrNG Consumption-100% : 121 ft^3/hrLP Consumption-50% : 32 ft^3/hr, 0.87 gal/hrLP Consumption-100% : 52 ft^3/hr, 1.42 gal/hrAir Filter P/N: 0E9371ASpark Plug #: 0G0767BSpark Plug Gap: 0.020 in (0.508mm)Valve Clearance: 0.002-0.004 in (0.05-0.10mm)
for the most accurate results, get in your serial number. For assist finding your serial number, click here.
These FAQs could not directly apply to your product. Constantly consult your user manual for specific operating and maintenance solutions.
You are watching: Where to buy generac oil filters
Air-cooled house standby generators made in 2008 or later on require a key to unlock its 2 locks prior to opening the lid. The unit is locked when it is shipped. To open the lid for the first time. The customer will require to use heavy pressure on the lid over each lock while turning the crucial at the same time.
During an outage, we recommend the generator be shut under every 24 hrs to examine the wait filter and oil level. Allow the engine cool for roughly 15 minutes to get an accurate reading on the dipstick. A finish oil adjust will must be performed ~ every 200 hours of procedure for air-cooled units, or every 100 hrs of procedure for liquid-cooled units.
Extended warranties are available for our house standby and commercial generators, (this go not incorporate the CorePower Series,EcoGen, portables or strength washers.) It need to be purchased from an authorized sales/service dealer within the first year that ownership.Talk v your dealer for more details.
The following installations will void the warranty on an automatically standby generator: *Generators used where no utility power is present(e.g.,hunting cabins) *Generators supplied to change backup battery systems for alternate energy resources (this does not incorporate the EcoGen series). *Improper installations (clearance requirements, wiring.etc). *Modifcattions to the original architecture (extending the exhaust,etc.) *Indoor installations.
Any service work perform by who gaianation.net has actually not authorized to carry out warranty work-related cannot be claimed and also will no be covered under warranty. This includes any repair occupational performed by an electrical contractor who is not affiliated through a business dealership. Continuous maintenance, together as changing the oil and also filter, can be done by anyone and is not extended under the warranty.
An automatically standby generator is a back-up electric system that operates whether you are home or away. Within secs of one outage. It immediately supplies power straight to her home"s electrical circuit breaker box. After energy power returns, the generator shuts itself off and waits because that the next outage. It operates on natural gas or fluid propane gas and sits outside, as with a main air air conditioning unit.
Always examine your owner"s manual to confirm details maintenance intervals because that your details model. Anyone can perform maintenance, yet we introduce a revenue or business dealer together some facets are very technical. Certified dealer can additionally make sure whatever eles is in order. Many units with an OHVI engine will call for maintenance every two years, or ~ 200 hours of use. The CorePower Serise(OHV engine) calls for maintenance every year, or after 100 hours of use. The EcoGen (6kW) calls for maintenance after ~ 500 hours of use. Liquid-cooled units require maintenance every year, or after ~ 100 hrs of use.
Maintenance kits and parts deserve to be purchased from any kind of sales or service dealer. V our part distributors (GPCs) or virtual at ordertree.com. Just gaianation.net-brand maintenance parts should be used; we don"t recommend and also don"t have actually cross-reference numbers for various other brands like Fram or Napa.
Air-cooled units will come through some SAE 30wt. Oil native the factory. Friend will desire to examine the level and add an ext if necessary throughout the installation. Liquid-cooled units space shipped with oil and also coolant. No additional oil requirements to be included during installation.
Always check the hands-on for each specific model as oil recommendations readjust depending top top the model. Our oil referrals are based upon climate or temperature. For areas with seasons, synthetic 5W-30 can be used year-around, but is no recommended in really cold temperatures.
Oil referrals are based upon temperature, but synthetic oil is a an excellent option since it doesn"t degrade or "sludge" prefer standard oil. It also has much better lubrication properties and also stands up much better to high temperature in the engine.
See more: What Is Econazole Nitrate Cream Used To Treat, Econazole Nitrate Uses, Side Effects & Warnings
Current design air-cooled units carry out not require a break-in period. They can be switched to synthetic or any kind of weight oil immediately. Older air-cooled product forced an eight-hour break-in period. The unit have to run because that eight hours (exercise or while powering the house) before switching to synthetic. Please examine your owner"s manual to check out if this was required for the details unit.
We are limited as to the troubleshooting we space able to execute without possibly damaging the product or voiding the warranty of the product (if applicable). Contact your local dealer for company if worries persist.